Complete Builders Inc. - General,
531 Hidden Cir
North Salt Lake
Primary Contact: PETER WANKIER
ENVISION QUALITY ELECTRICAL, INC. - Electrical,
Primary Contact: ENVISION QUALITY ELECTRICAL, INC.
De Best Heating & Air - Mechanical,
Primary Contact: De Best Heating & Air
Platinum Plumbing Services Inc - Plumbing,
Parcel #: 16323520020000
718 E 3900 S
106 E EDGECOMBE DR
SALT LAKE CITY UT,
Completed - Shirl White
Completed Date: 01/23/2020
Denied - Rich Novasio
Completed Date: 02/04/2020
- 1St review
02/05/2020 - In order complete your review the following questions need to be addressed. Using the 2018 IEBC (International Existing Building Code) Section 301. (1) Please chose the method being used to design and alter the building (301.3.1 or 301.3.2 or 301.3.3).
(2) Determine the occupancy based on Sq Ft or seating capacity, the area of storage is not consistent with noted sq ft.
(3) The current layout of the building does not share same uses on each floor, justify no elevator access
(4) The removal of walls in the "garage area" is there any structural or framing plans?
(5) Need to determine fire wall location or use compliance methods to delete "justify" and note on plans
(6) Cannot vent over sidewalks (water heaters/dryers).
(7) Any venting through roof will require separation from existing equipment
In order to complete your request for a plan review please address the following questions, update plans and re-submit to: firstname.lastname@example.org please attach permit number